### Abstract

In VSC-based microgrids which employ the frequency/voltage droop control method, the power sharing controllers alter the frequency and magnitude of each VSC output voltage based on the output active and reactive power, respectively. This method employs the variable voltage and frequency instead of physical communication link in order to active and reactive power sharing. Since there is no communication link, and the voltage and frequency are not constant in different load conditions, and no DG is large enough to provide all the demand variations, the PV bus model and slack bus model cannot be employed in these networks. Hence the conventional power flow method is not appropriate to calculate the steady state solution in such microgrids. As a result, previous works in this area in order to obtain the steady state solution perform a time domain simulation, which is very time-consuming process for this purpose. Therefore, developing new methods that calculate the steady state solution in a suitable time is a necessity. This paper presents a new approach to construct power flow equations in these networks without PV and slack bus model. The steady state solution of these equations is calculated, and the operating point is obtained much easier and faster than time domain simulation algorithm. In order to validate the proposed method, the time response of the proposed equations is compared with the time domain simulation results of PSCAD/EMTDC, which is an electromagnetic transient simulation program. The comparison indicates that the results of the proposed method, is very accurate. Moreover, the calculation time of this method outperforms other time domain simulation based method.

Original language | English |
---|---|

Pages (from-to) | 3041-3050 |

Number of pages | 10 |

Journal | International Review of Electrical Engineering |

Volume | 6 |

Issue number | 7 |

Publication status | Published - 1 Nov 2011 |

MoE publication type | A1 Journal article-refereed |

### Fingerprint

### Keywords

- Autonomous microgrid
- Distributed generation
- Frequency/voltage droop
- Load sharing
- Power flow algorithm
- Small signal stability
- Voltage source converter

### Cite this

*International Review of Electrical Engineering*,

*6*(7), 3041-3050.

}

*International Review of Electrical Engineering*, vol. 6, no. 7, pp. 3041-3050.

**Decentralized VSC-based microgrid's general power flow.** / Hasanpor Divshali, P.; Hosseinian, S. H.; Abedi, M.

Research output: Contribution to journal › Article › Scientific › peer-review

TY - JOUR

T1 - Decentralized VSC-based microgrid's general power flow

AU - Hasanpor Divshali, P.

AU - Hosseinian, S. H.

AU - Abedi, M.

PY - 2011/11/1

Y1 - 2011/11/1

N2 - In VSC-based microgrids which employ the frequency/voltage droop control method, the power sharing controllers alter the frequency and magnitude of each VSC output voltage based on the output active and reactive power, respectively. This method employs the variable voltage and frequency instead of physical communication link in order to active and reactive power sharing. Since there is no communication link, and the voltage and frequency are not constant in different load conditions, and no DG is large enough to provide all the demand variations, the PV bus model and slack bus model cannot be employed in these networks. Hence the conventional power flow method is not appropriate to calculate the steady state solution in such microgrids. As a result, previous works in this area in order to obtain the steady state solution perform a time domain simulation, which is very time-consuming process for this purpose. Therefore, developing new methods that calculate the steady state solution in a suitable time is a necessity. This paper presents a new approach to construct power flow equations in these networks without PV and slack bus model. The steady state solution of these equations is calculated, and the operating point is obtained much easier and faster than time domain simulation algorithm. In order to validate the proposed method, the time response of the proposed equations is compared with the time domain simulation results of PSCAD/EMTDC, which is an electromagnetic transient simulation program. The comparison indicates that the results of the proposed method, is very accurate. Moreover, the calculation time of this method outperforms other time domain simulation based method.

AB - In VSC-based microgrids which employ the frequency/voltage droop control method, the power sharing controllers alter the frequency and magnitude of each VSC output voltage based on the output active and reactive power, respectively. This method employs the variable voltage and frequency instead of physical communication link in order to active and reactive power sharing. Since there is no communication link, and the voltage and frequency are not constant in different load conditions, and no DG is large enough to provide all the demand variations, the PV bus model and slack bus model cannot be employed in these networks. Hence the conventional power flow method is not appropriate to calculate the steady state solution in such microgrids. As a result, previous works in this area in order to obtain the steady state solution perform a time domain simulation, which is very time-consuming process for this purpose. Therefore, developing new methods that calculate the steady state solution in a suitable time is a necessity. This paper presents a new approach to construct power flow equations in these networks without PV and slack bus model. The steady state solution of these equations is calculated, and the operating point is obtained much easier and faster than time domain simulation algorithm. In order to validate the proposed method, the time response of the proposed equations is compared with the time domain simulation results of PSCAD/EMTDC, which is an electromagnetic transient simulation program. The comparison indicates that the results of the proposed method, is very accurate. Moreover, the calculation time of this method outperforms other time domain simulation based method.

KW - Autonomous microgrid

KW - Distributed generation

KW - Frequency/voltage droop

KW - Load sharing

KW - Power flow algorithm

KW - Small signal stability

KW - Voltage source converter

UR - http://www.scopus.com/inward/record.url?scp=84858041585&partnerID=8YFLogxK

M3 - Article

VL - 6

SP - 3041

EP - 3050

JO - International Review of Electrical Engineering

JF - International Review of Electrical Engineering

SN - 1827-6660

IS - 7

ER -